A garage within a small commercial building has radiant heat only. Since radiant heaters do not warm the air but rather only any physical object that is in the direct path of heat transfer, I've never relied upon them for maintaining correct temperature around a fire sprinkler system.
Have you used radiant heat to maintain temperature in a wet system? NFPA 13 (2016 Edition) 188.8.131.52.1 calls for temperature reliably maintained at or above 40 degrees F (4 deg C) for a wet system, which I would not believe would be the case for radiant heat.
Posted anonymously by a member for discussion. Discuss this | Submit a Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
August 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.