The 2019 Edition of NFPA 1221 (Standard for the Installation, Maintenance, and Use of Emergency Services Communications Systems) Section 4.5.2 requires that communication centers "be provided with an automatic fire detection, alarm and notification system in accordance with NFPA 72."
But what constitutes "automatic fire detection?"
I'm thinking this is alluding to wanting full smoke coverage of the area/space but the language of "fire detection" seems intentionally vague. A supervised automatic suppression system would meet this definition I think; its seems excessive to think a constantly attended room with fully sprinkler coverage would also require full smoke detection.
Is there some other guidance I need to consider here? Is this defined elsewhere?
Thanks in advance.
Sent in anonymously for discussion. Click Title to View | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top Feb 2023 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES