My clients are wanting to store a small amount of Class IIIB liquid (cooking oil) in a Group S storage mezzanine that is part of a larger Group F-1 commercial cooking facility. I've done the larger FP scheme for when this product becomes a full-scaled production with its own designated processing plant, and that has a rack protection scheme for Intermediate Bulk Container storage.
This smaller-scale renovation is a mock-up of the larger scale production in an existing plant- intended to get product to the customers for test marketing. The quantity stored will be a single pallet of (60) 5 gal plastic jug in box containers. The overhead system is Ordinary Hazard Group 2, although if I source calculated I could probably get a .6 x 3000 +500.
Because the quantity is so low, nothing in NFPA 30 seems to really pertain to the storage. The jurisdiction is on the 2012 IFC, and I think that §5704.3.4.4 applies. It basically says that flammable and combustible equipment for maintenance and the operation of equipment in excess of 10 gal shall be stored in liquid storage cabinets (the equipment of course being the searing/frying equipment in the other area of operation).
My question arises from never having to have specified protection criteria for storage quantities so small. I want to get the client to unload the pallets into 3- cabinets, following all of the separation criteria.
Does use of the cabinets mean that the fire-rating requirements for "control areas" do not need to be followed?
Or does the standard want the storage cabinets inside a burn-rated area?
If it is the latter, I am planning to ask the fire marshal for an exemption for the 1-hr burn rating required by NFPA 30 Table 9.7.2.
Posted anonymously by a member for discussion. Discuss this | Submit a Question | Subscribe
Subscribe for posts on PE Problems and Daily Discussions, straight to your inbox, for free:
Thank You to Our Top February 2019 Contributors!
Ask your question here (members area)
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.