We have a project with a comment from the AHJ stating that the dryer vent cannot terminate to the exterior condominium wall, which is the egress wall for the condominium exit exterior breezeway on that floor.
We're under NFPA 101 (regarding Section 30-3.6.3 for Unprotected Openings).
Is a duct penetration considered an unprotected opening?
Dry vents cannot have fire/smoke dampers, so can it just be a metal duct?
Sent in anonymously for discussion. Click Title to View | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top April '22 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES