What is the requirement for standpipes on the top level of a fully-sprinklered, open parking garage?
On the covered levels that are sprinklered, the hose travel distance is allowed to be 200 feet based on NFPA 14-2013 Section 126.96.36.199. For levels that are not sprinklered (the top level is open to the sky), the same NFPA section states the hose travel distance is 150 feet.
So, on a 6 level parking deck I've got standpipes located such that 200 foot hose travel distance is accomplished on the covered/sprinklered levels. What happens when I get to the top/open level?
Posted anonymously by a member for discussion. Discuss this | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
April 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
2019 PE Prep Guide
PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.