We are currently working on a project with a building height of 36-feet that currently has K16.8 ESFR sprinklers installed to protect open rack storage of Class I-IV commodities at 12-feet in height.
The hydraulic calculations are based on Ordinary Hazard Group 2, with a 0.20 gpm/sqft density over 1,500 sqft with a starting pressure of 7 psi. The design area is based on 18 ESFR sprinklers flowing at 100 sqft per sprinkler. The total sprinkler demand is 834 gpm.
They are calling this an "ESFR-Ready" sprinkler system.
It seems to me that the building height would drive the starting pressure for this scenario and the calculation should actually be 12 sprinklers with a minimum starting pressure of 52 psi when using K16.8 ESFR sprinklers. This comes after examining Chapters 12-20.
What would the lowest starting pressure be for K16.8 ESFR sprinklers protecting open rack storage of Class I-IV commodities to 12-feet in height with a building height of 36-feet?
Sent in anonymously for discussion. Click Title to View | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
February '21 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.