We traditionally have specified closed wye-delta transition starters for electric fire pumps on our projects. The fire pumps typically consist of horizontal split-case electric pumps between 500 and 1,500 gpm.
In the past, we've felt that the closed wye-delta starter offered a good balance of cost (less than soft-start but more than open delta wye) against the impact it has on backup generator sizing (helps generators size more than an open-wye delta but not as much as soft start).
Is soft-start still significantly more expensive than delta-wye closed transition starters?
I am hearing that the cost of soft-starters may have come down significantly and we try to be open-minded to what the industry is offering if we're in the wrong.
Posted anonymously by a member for discussion. Discuss this | Submit a Question | Subscribe
Subscribe and learn something new each day:
Top Dec. '21 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES