Does the "small room rule" apply to sidewall sprinklers?
Posted anonymously by a member for discussion. Discuss this | Subscribe.
11/16/2018 10:22:28 am
No, unfortunately since it appears under the NFPA #13 section number for standard pendent and upright spray sprinklers, and does not appear in the following section for sidewalls, it is my belief that the "small room rule" (for spacing 9-ft. off a single wall, or for averaging the area of coverage for sprinklers within the room) cannot be applied to sidewall sprinklers.
Leave a Reply.
Subscribe and learn something new each day:
Top Feb 2023 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES