Question on seismic bracing for fire sprinkler:
126.96.36.199 Sway Brace Installation
188.8.131.52.10 C-type clamps including beam and large flange clamps with or without restraining straps, shall not be used to attach braces to the building structure.
I typically see Cooper B-line fig.828 used, the universal seismic clamp on the beam flange. Do they have to be used with a retaining strap on the beam? Manufacturer's instructions is silent in this regard.
Note: This is a Daily Discussion question submitted anonymously to us. Submit a Question or Discuss This Here.
Subscribe for posts on PE Problems and Daily Discussions, straight to your inbox, for free:
Thank You to Our Top January '19 Contributors:
Ask your question here (members area)
Get all-access to the downloadable Toolkit, Sprinkler Database, Ask-A-Question and more.
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.