A project that contains a light hazard office space with a dry-pipe sprinkler system, and a 900 sqft area with sloped ceilings (about a 5/12 pitch). Per NFPA 13, the remote area should increase by 30% for the dry system (NFPA 13-2013 Section 22.214.171.124.5) and another 30% for the slope (NFPA 13-2013 Section 126.96.36.199.4). However, does the fact that only 900 sqft of the entire remote area is sloped impact the overall size of the remote area at all? Curious in other's opinions.
Note: This is a Daily Discussion question submitted anonymously to us. Submit a Question or Discuss This Here.
Subscribe and learn something new each day:
Thank You to Our Top
April 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
2019 PE Prep Guide
PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.