I have a question that stems from NFPA 318 (Protection of Semiconductor Fabrication Facilities), Chapter 11, Section 188.8.131.52.
184.108.40.206* Automatic sprinklers for cleanrooms or clean zones shall be installed in accordance with NFPA 13, and shall be
hydraulically designed for a density of 8.15 L/min·m2 (0.20 gpm/ft2) over a design area of 278.8 m2 (3000 ft2).
For a clean room 220.127.116.11 mentions 0.20 gpm/sqft density over 3,000 sqft design area. We're considering quick-response standard-spray sprinkler coverage under section 18.104.22.168. The client is requiring a double-interlock pre-action system, so under NFPA 13 22.214.171.124.5 the remote area must be increased by 30% without revising the density.
Can we omit the 30% increase in sprinkler operation under NFPA 13 126.96.36.199.3 since we are using quick response sprinklers?
Submitted anonymously and posted for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top October '23 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES