In general, when designing fire sprinkler systems with a fire pump, is your philosophy to only provide the minimum fire pump size that is needed to support your system, or do you often increase the fire pump size to decrease pipe sizes on the system?
How much are you typically willing to increase a fire pump size in order to benefit the pipe sizes throughout your project?
When I first learned about how to size a fire pump, I was told that if your system gets over 100 psi then you might as well size the pump to get as close to 170-175 psi on the system as possible - the reason being that the cost to upsize a fire pump is less than the savings associated with smaller mains and branch pipe.
I'm not sure that there's a hard-and-fast rule of thumb, but I'm just interested if other people use the same strategy or if it's entirely dependent on the type of job and size of the job.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
October '20 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.