A project site is connected to a water tank through an equivalent 650 feet of 6-inch schedule 10 pipe (c-factor of 140). If the water tank is 165 feet above the project site, the fire flow available at the project site is most nearly:
a. 1,300 gpm
b. 2,100 gpm
c. 2,400 gpm
d. 8,700 gpm
Solution | Posted 10/10/18
Subscribe for posts on PE Problems and Daily Discussions, straight to your inbox, for free:
Thank You to Our Top January '19 Contributors:
Ask your question here (members area)
Get all-access to the downloadable Toolkit, Sprinkler Database, Ask-A-Question and more.
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.