A new Type II (000) construction facility without exposure protection is being designed to be built on an industrial campus. If Class II liquids are planned to be handled and dispensed regularly within the facility, what minimum distance from an adjacent, build-able property must the building allow?
a. 5 feet
b. 10 feet
c. 25 feet
d. 50 feet
Solution | Posted 06/13/19
Note: Sorry, I did it again with a daily question. NFPA 30 is no longer a required reference and this problem would not be eligible to be used for the 2019 exam.
Subscribe and learn something new each day:
Thank You to Our Top
February '21 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.