A Level 2 Aerosol is to be boxed and stored on pallets at 15 feet with a ceiling height of 26 feet. Which of the following sprinkler protection criteria is acceptable?
a. Standard Spray (K-factor at least 8.0) Sprinklers; 0.30 gpm/sqft over 2,500 sqft
b. ESFR upright K14.0, quick-response, 12 sprinklers at 50 psi
c. ESFR pendent K16.8, quick response, 12 sprinklers at 35 psi
d. ESFR pendent K22.4, standard response, 12 sprinklers at 25 psi
Solution | Posted 09/05/18
Subscribe for posts on PE Problems and Daily Discussions, straight to your inbox, for free:
Thank You to Our Top January '19 Contributors:
Ask your question here (members area)
Get all-access to the downloadable Toolkit, Sprinkler Database, Ask-A-Question and more.
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.