In an NFPA 13R system does the FDC check valve need to be accessible?
In 13 it states it is required, but I can't find it in NFPA 13R. Section 6.11.4 talks about ball drip for check valve, but I do not see anything on accessible. I’m sure I’m missing some code path that references 13 possibly? Thanks.
Submitted anonymously and posted for discussion. Discuss This | Submit Your Question | Subscribe
Leave a Reply.
Subscribe and learn something new each day:
Top Feb 2023 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES