A small, wood-structure apartment complex is getting an NFPA 13R fire sprinkler system. Based on hydraulic calculations, the incoming water service only needs to be 2-inch, and the backflow can be as small as 1-1/2-inch.
Many backflow preventers with indicating butterfly valves don't get down to the 1-1/2-inch size - rather many of the small backflows only have ball valves which I'm not sure can actually be supervised.
Are the valves on a backflow preventer for an NFPA 13R system required to be supervised? Is there ever a case where the backflows can use ball valves on an NFPA 13R system?
Posted anonymously by a member for discussion. Discuss this | Subscribe
Subscribe and learn something new each day:
Top Jan '23 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES