I'm currently working on a project for a packaging factory in which there are rooms which are used for storage of Milk and Juice in stainless steel tanks that are about 1.5 m (4.9 ft) in diameter and 8 m (26.2 ft) in height.
There are about 5-6 tanks for each area (milk and juice storage). Each room is about 70 sq.m. (753.4 sqft). The ceiling height is about 11.1 m (36.4 ft). The content combustibility (i.e. Milk & juice) is low and the quantity is high. Since the height of the tanks is above the threshold of 3.7 m (12 ft), I cannot consider it to be protected by LH or OH1 curves and it should come under storage occupancy and commodity classes.
Since my exact requirement is not present in the list of commodity classes in NFPA 13, I figured it to be Class 1 per the liquid content. Accordingly, it would be under Commodity Class 1 curve in NFPA Chapter 14 Figure 18.104.22.168 (2013 Edition) and multiplication factor for density vs storage height from Figure 22.214.171.124.
Kindly let me know if I'm on the right track or if there is something which I overlooked.
Note: This is a Daily Discussion question submitted anonymously to us by a Toolkit member. Discuss This Here.
Subscribe for posts on PE Problems and Daily Discussions, straight to your inbox, for free:
Top October Contributors:
Ask your question here (members area)
Get all-access to the downloadable Toolkit, Sprinkler Database, Ask-A-Question and more.
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.