What is the lowest demand pressure and flow you've come across for an ESFR system?
Looking big-picture at owner storage options early in a project (when we might have an idea on available pressure but don't yet have a plan to work from), the minimum flow and pressure we've come across as a minimum was 73 psi at 1,450 gpm. It was using (12) K25.2 sprinklers at 15 psi (minimum storage heights and a 250 gpm hose allowance). If we don't even have this supply, I typically anticipate a fire pump.
Have you seen any demands lower than this?
Posted anonymously by a member for discussion. Discuss this | Subscribe
Subscribe and learn something new each day:
Top April '22 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES