A locker room (1050 ft²) in apartment building is divided into small storage compartments. No shelves, no lifting devices. The ceiling height is 9’.
The sprinkler system design criteria was chosen as OH II, which is adequate for miscellaneous storage of Class IV Commodities up 12 feet in height as well as Plastic up to 5 feet.
Now the AHJ is requesting either design of plastic protection up 8 feet saying that some plastic may be stored - therefore we have to treat this as storage of mixed commodities - therefore it shall be protected by the requirements of highest classified commodity, or provide assurance that no plastic will be stored.
Will “mixed commodities” be applicable for miscellaneous storage? Or do we not have any grounds for argument?
Posted anonymously by a member for discussion. Discuss this | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
August 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.