We manufacture dust collectors and pre-pipe fire sprinklers within them with a couple fusible fittings.
We pressure test the pipe at our shop, however, when a contractor connects to them in the field, are there any code/standard requirements to check the system for leaks after connecting to the system?
We put on our drawings that the contractor should test for leaks, however, we're trying to determine what requirements exist for this application.
The problem we're running into is that the connection is supposed to be made and checked before installing cartridges. If a leak occurs, the contractor could address and not get the paper cartridges all wet with running water down at the floor. In this last case they didn't, and I'm trying to address future installation of systems and make sure the contractor checks for leaks.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
June 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.