I am looking at a project that shows 6-inch underground lead-in to a riser room. The specs however call out the install of a 1,000 gpm pump. NFPA 20 shows that for a 1,000 gpm pump suction sizing should be no less than 8-inch diameter.
Is a 6-inch even allowed for this application?
Sent in anonymously for discussion. Click Title to View | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top Jan '23 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES