We have been asked if a 20+ year old wet pipe sprinkler system we installed into a paint application room is the correct method of protection for a specific paint product that is currently being used.
The MSDS sheets for a few of the products they now use indicate protection with dry chemical, foam, or water fog.
I have been told that the MSDS sheets typically refer to the product as its being stored and not necessarily as its being applied. The storage is not happening in this room of course, but in approved fire-rated storage cabinets outside the area. None of the typical requirements for alternate protection are met per NFPA 33.
Basically other than the product data sheets, this is a run of the mill paint application area. Nothing automated or fancy.
Anyone have any experience with a similar situation?
Sent in anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top Jan '23 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES