I'll preface this that I'm not a engineer. There is 17-foot storage with an existing sprinkler design of 0.20 / 1,500 sqft.
Based on NFPA 13, I believe we would need 0.21 / 2,000 sqft for a Class II commodity (non-encapsulated rack storage).
How would you recommend going about increasing both the remote area size and the density on an existing system?
Sent in anonymously for discussion. Click Title to View | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top August '21 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES