We have five, two-car-high stacking units in a basement area. We have a smoke exhaust system but also need an active protection system.
NFPA 13 categorizes such arrangements as Extra Hazard (Group 2).
Does anyone have experience of what would be an acceptable layout around these areas as the NFPA 13 guidance is not extensive?
Subscribe and learn something new each day:
Top Jan '23 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES