When performing hydraulic calcs for NFPA 13 residential occupancies, what is the best approach to address small Ordinary Hazard rooms, such as janitor's closets or laundry rooms located on an otherwise-residential floor?
Room design is not always an option due to the prerequisites listed in NFPA 13, but area/density seems excessive when the calculation method given for residential occupancies is the 4 most demanding adjacent heads.
A 1,500 square foot area seems to go well beyond this approach, defeating the purpose of the residential design method. Other than room design, is there a justifiable code basis for calculating only the heads in the most demanding ordinary hazard room on such a floor?
Submitted anonymously and posted for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
August 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.