We're designing a fire sprinkler system for plastic (Group A material, unexpanded polyethylene) recycling site. We are designing only for the depot area. There are raw materials stored as solid blocks up to ...We've raw material stored as solid blocks up to 12 feet (3.6 meters).
I am thinking this should be considered rack storage under NFPA 13 Section 184.108.40.206 (2016 Edition) for Protection Criteria for Rack Storage of Class I Through Class IV Commodities Stored Up to 12-ft (3.7m) in Height.
Am I wrong considering this? Note that compacted material will have a lower combustion propagation velocity than generic goods. Any ideas? Thanks in advance.
Submitted anonymously and posted for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
October '20 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.