Is it acceptable to place the connection for the fire pump test header on the 'system' side of the isolation valve?
I've seen instances of this and it concerns me that there is a potential to render the FDC ineffective during pump testing; not to mention the possible corruption of pump test data due to the influence of the 'stored' water and pressure in the existing sprinkler system.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top Jan '23 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES