I'm new to this industry and I've been really trying to pick apart NFPA 13.
I have a question related to determining the area of sprinkler operation of a dry pipe system with high temperature sprinklers. The system is providing coverage of an outdoor chemical storage canopy.
Dry System due to freeze potential
Extra Hazard Group 1 (0.30 gpm/sf over 2500 sf) per NFPA 13 Fig. 184.108.40.206.1
High temperature rated sprinklers per NFPA 13, Section 220.127.116.11.4
My question is regarding adjustments to the area of sprinkler operation. Dry systems are to be increased 30 percent per 18.104.22.168.5, then it states in 22.214.171.124.6 that the area can be reduced by 25 percent when using High temperature sprinklers. Multiple adjustments can be compounded.
Increase: 2500*30% = 750 sf
Decrease: 2500*25% = 625 sf
2500 + 750 - 625 = 2625 sf
A conservative approach would be to ignore the 25% reduction, but I'm curious what is actually required per code.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
April 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
2019 PE Prep Guide
PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.