NFPA 13 has the hydraulic remote area reduction for use of Quick-Response sprinklers for wet, light/ordinary hazard, low(er) ceilings without pockets.
Does FM Global recognize anything similar for the use of quick-response sprinklers, or is their HC-1, HC-2, and HC-3 categorization the minimum remote area size regardless of sprinkler RTI?
I've checked FM Global Data Sheet 2-0 and 3-26, but have yet to find anything similar in nature.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top Sept. '21 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES