I have a question id like a second opinion about. I have a client with a new build boat storage facility, approx 30 ft high, at one end on the ground floor is an office area with a suspended ceiling. The installers have used U-Bolt Mechanical Tee couplings to attach the drops to the branch line, and then hung 20-ft of 1" pipe as the drop.
What is the correct way to secure these drops?
There is currently no lateral or vertical support. This is not in a seismic area.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
August 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.