NFPA 13 requires closely spaced sprinklers with a draft curtain around unenclosed moving stairways, staircases, or similar unenclosed floor openings which are not large (20 feet or more across and 1000 sqft or greater), as an alternative to the enclosure of the vertical opening (NFPA 13 18.104.22.168 in 2016 and 22.214.171.124 in 2019).
This seems to jive with NFPA 101, but where does it come into play with the International Building Code?
As a sprinkler designer I want to be cognizant of situations where closely spaced sprinklers and draft curtains are necessary, but would they only surface as an AHJ-approved code alternative by IBC 104.11 (Alternative materials, design and methods)?
Posted anonymously for discussion. Discuss This | Submit a Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top
June 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.