For a horizontal manifold that contains multiple sprinkler systems, are check valves needed for each sprinkler system? In this case there are no standpipe systems in the building.
As I understand it, NFPA 13 only requires a check valve on the incoming fire department feed, but each of the different system risers have no requirement for a check valve.
Posted anonymously by a member for discussion. Discuss this | Subscribe
Subscribe for posts on PE Problems and Daily Discussions, straight to your inbox, for free:
Thank You to Our Top February 2019 Contributors!
Ask your question here (members area)
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.