Have you had AHJ’s request FPE seals on hood fire suppression systems often? It’s in the letter of UFC 3-600-01 (this is a US military project) but has not come up before for us.
Do you have an opinion on what needs to happen if the system (or the majority of it) is factory installed in the hood? Can it be treated as part of the UL listed assembly?
Posted anonymously by a member for discussion. Discuss this | Submit a Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top September Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
2019 PE Prep Guide
PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.