Many two-inlet (2 x 2-1/2") fire department connections I'm familiar with and commonly have a single-clapper, where the clapper will swing and cover the inside of the inlet on the side of the FDC not being used to prevent flow out of the other inlet.
Is there any advantage to having a double clapper?
One disadvantage I see is that you can't forward-flow test the backflow preventer out the FDC if there are clappers for each inlet.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top September Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
2019 PE Prep Guide
PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.