I hope you are having a great week.
This week is a 2020 update to a popular post from 2016 with a free PDF cheatsheet. It's usefully for novice designers or experienced inspectors, with clear code references and purposes of each of the components that go into a floor control assembly serving a fire sprinkler system.
A breakout of each of the components that go into a fire sprinkler floor control assembly.
If you find any of these tools helpful, consider sharing with a friend or colleague and nudge them to subscribe for more tools and tips like this here: www.meyerfire.com/subscribe. Thanks in advance!
Today we're breaking into floor control assemblies. The following is a full arrangement for a combination standpipe/sprinkler riser where high pressures necessitate a pressure reducing valve at each level.
While every element in this specific arrangement is certainly not a necessity on every project, here's some considerations that go into the requirements and considerations for a layout like this:
Auxiliary Drain Valve
Want to see more like this? Subscribe to our Blog.
Get Free Articles via Email:
+ Get calculators, tools, resources and articles
+ Get our PDF Flowchart for Canopy & Overhang Requirements instantly
+ No spam
+ Unsubscribe anytime
Joe Meyer, PE, is a Fire Protection Engineer out of St. Louis, Missouri who writes & develops resources for Fire Protection Professionals. See bio here: About