Last week we debuted a remote area cheatsheet detailing some tips for quick-response reduction, slope adjustments, and dry, double-interlock pre-action and storage area adjustments.
We're all about bringing fire protection pros around the world together (globally), and so today I'm happy to also add a metric version of this same cheatsheet. We plan do to updates like this with our content going forward.
To download, just click below. If you're a University user, you can get all of our latest cheatsheets, checklists and summaries under your University Dashboard. Thanks & have a great week!
This Remote Area cheatsheet allows for quick adjustments to the remote area and minimum remote-area widths when conducting or reviewing fire sprinkler hydraulic calculations.
It's been too long since our last cheatsheet! Happy to bring about a new one to the table today.
One number that I seem to always need to crunch when laying out or reviewing fire sprinkler systems is the remote area adjustments, and the minimum width of a remote area. This applies specifically to the Density/Area method of Hydraulic Calculations in NFPA 13.
The formula is simple enough, w = 1.2 x sqrt(remote area size), where w is the minimum remote area width, and the remote area size is our final adjusted remote area that we're using.
Now for a routine calculation with a remote area of 1,500 sqft, I pretty much have the 46.5-foot area width memorized. Why is it important? The minimum width dimension tells us how wide our remote area needs to be. It's the dimension parallel to the branch lines, that captures as many sprinklers as it can along the branch line.
We take this minimum area, see how many sprinklers this area covers, and round up to the next whole sprinkler. It's our minimum width dimension that we're not allowed to reduce.
The 46.5-foot dimension might be easy enough to remember, but what about when a remote area is reduced using the quick-response reduction? What if the ceiling is also sloped?
Adjustments to the remote area are a process on their own, and each have implications for the minimum remote area width.
If you're using our Toolkit you already know we have tools that will compound the calculations for you. Our Quick-Response Reduction tool will adjust the remote area size based on the ceiling height, and our System Estimator tool will adjust for quick-response, sloped ceilings, dry and pre-action systems, high-temperature sprinklers, and more:
But, there are still times where I just want to quickly glance at my remote area size and translate that into a minimum width. That's what today's cheatsheet is all about.
This quick reference PDF helps address a few things:
I hope this one is helpful for you as conduct or review hydraulic calculations on your projects. Any tips, feedback or improvement ideas, be sure to let me know.
Thanks & have a great rest of your week!
First - you don't read articles here for my political or personal opinions, and I get that. I respect that. I very much appreciate that.
That said, I worry for my friends colleagues in Ukraine and Russia. I'm heartbroken about what they are going through right now, of which I can't imagine. I have a wife and three kids. I work with people in Ukraine who have the same young families. This past week has been tough. Nothing I feel here remotely compares to what they are facing right now. I just cannot imagine having to choose between fleeing my home country for the safety of my family or grabbing a rifle. I can't imagine it.
I wish we, as humans, could find ways to appreciate and support each other instead of violence. I wish we better embraced a perspective of mutual concern for each other over destruction. What are we - in our collective bond for fire protection - if not a group of people trying to find ways to create safe environments for public well-being? To help others? To save lives?
We're connected now. I work with people in the U.S. and all across the world - by choice - and I'm just starting to appreciate what a global attitude adds to my life. Because of this website I get to talk with fire protection people around the world, and get to hear about some of the challenges they face. We're not that different.
I don't want to pretend that my own country's history is flawless - that even our recent record is faultless. I cannot be the one to "cast the first stone." I simultaneously celebrate being an American but recognize that we have a long way to go. I pray for Ukraine and everyone involved in the conflict. I pray that our leaders, everywhere, and in any capacity, find a way to end violence quickly and recognize the value of the lives of the people they are affecting.
I genuinely wish that we all (myself included) could better appreciate each other and find ways to help and not hurt. I know you don't come here for my take, but I do appreciate you. Thank you for being here, for caring, and for being a part of our greater community that is working to make good in the world.
Get Free Articles via Email:
+ Get calculators, tools, resources and articles
+ Get our PDF Flowchart for Canopy & Overhang Requirements instantly
+ No spam
+ Unsubscribe anytime
Joe Meyer, PE, is a Fire Protection Engineer out of St. Louis, Missouri who writes & develops resources for Fire Protection Professionals. See bio here: About