Have a unique scenario I'd be interested in other's take on. Eight-story building with automatic standpipes and a fully-sprinklered building. There's multiple scenarios where the building is close enough to an adjacent building that the exterior wall needed to be rated. In order to keep the fire resistance rating Tyco window sprinklers were installed in conjunction with glass to provide up to a 2-hour fire resistance rating.
The issue is that the sprinkler system experiences a working pressure of up to 220-230 psi, while the window sprinklers are only available as rated up to 175 psi.
We've proposed adding pressure reducing valve to the seven floors affected by this situation, but that introduces its own issues aside from cost. We've also suggested replacing the glass with a rated glass.
Are there other alternatives we haven't explored here? Would be interested in others' opinions.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top September Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
2019 PE Prep Guide
PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.