We have a two story apartment building, and we are installing an NFPA 13R wet pipe sprinkler system.
Is an outside hose demand required to be included within the calculations?
There are no inside hose stations.
If outside hose demand is required, is the demand the same as light hazard? 100 gpm?
We couldn't find a reference to this in NFPA 13R.
Sent in anonymously for discussion. Click Title to View | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top June '21 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES