An existing, non-sprinklered 2,800 sqft single-story building is divided into (2) 1,400 sqft restaurants. The division between the restaurants is a 2-hour rated wall.
The owner would like to remove the dividing wall to create a single 2,800 sqft restaurant. Will the removal of this wall prompt a requirement for sprinklers to be installed in the building? This project is under the International Building Code.
Subscribe and learn something new each day:
Thank You to Our Top
August 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.