NFPA 13 (2019) Section 184.108.40.206 states that quick-response sprinklers shall not be mixed with any standard-response within a compartment unless some conditions apply.
220.127.116.11 Where quick-response sprinklers are installed, all sprinklers within a compartment shall be quick-response unless otherwise permitted in 18.104.22.168, 22.214.171.124, or 126.96.36.199.
Those conditions don't apply in my case and I know there's a definition of a compartment in 3.3.38.
However, from a practical standpoint if the compartment in question is a corridor, would you include the adjoining offices in the compartment? These offices are likely to have their doors open and are not on any magnetic door closing devices.
Posted anonymously for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top July '22 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES