NFPA 13 (2010 Edition) 21.23 Cleanrooms: 188.8.131.52 Automatic sprinklers for cleanrooms or clean zones shall be hydraulically designed for a density of .20 gpm/sqft over a design area of 3000 sqft.We have a wet pipe system utilizing quick-response sprinklers.
With an ordinary hazard density (.20 gpm/sqft) would I be allowed to use the quick-response design area reduction in Chapter 11?
Submitted anonymously and posted for discussion. Discuss This | Submit Your Question | Subscribe
Subscribe and learn something new each day:
Top Sept. '21 Contributors
Get 100 Days of Free Sample Questions right to you!
PE PREP SERIES