Which of the following is typically not considered obstructed construction for fire sprinkler design?
a. concrete tees with solid members 5 inch wide and 2 ft tall
b. heavy timber construction with 4 inch solid wood beams
c. beam and girder construction with 6 inch steel beams 6 ft apart
d. panel construction with panels under 300 sqft
Solution | Posted 10/07/20
b. heavy timber construction with solid wood beams, per NFPA 13-2016 A.3.7.2 as unobstructed construction. Concrete tees, beam and girder construction, and panel construction as described all fit the associated definitions of obstructed construction in NFPA 13 A.3.7.1 (2), (1) and (4) respectively.
Subscribe and learn something new each day:
Thank You to Our Top
September '20 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.