A class III commodity is encapsulated and stored on shelves within a large walk-in cooler. A dry system is being designed to serve this hazard. If the storage is anticipated to be 13 ft. in height with a 17 ft. ceiling, determine the required design density with the smallest remote area for high temperature sprinkler protection using the Control Mode Density/Area approach.
a. 0.14 gpm/sqft / 2,000 sqft
b. 0.14 gpm/sqft / 2,600 sqft
c. 0.15 gpm/sqft / 2,600 sqft
d. 0.18 gpm/sqft / 2,600 sqft
Solution | Posted 09/15/20
Subscribe and learn something new each day:
Thank You to Our Top
February '21 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.