A new healthcare building is being designed with a suite with no sleeping areas and full smoke detection. What is the required construction for the corridor walls?
a. smoke partition only
b. smoke barrier only
c. 1-hour fire resistance and smoke barrier
d. none of the above
Solution | Posted 09/03/20
d. None of the above, in accordance with NFPA 101-2018 22.214.171.124.3. The suite corridor walls are required to resist smoke, but are specifically not required to be a smoke barrier or smoke partition as identified in the Annex Section A.126.96.36.199.3.
Subscribe and learn something new each day:
Thank You to Our Top
August 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.