A remote camp facility is being planned which intends to operate seasonally. Due to the remote nature of the site and lack of easy access to nearby mains, a water storage tank is being considered to supply the site fire sprinkler systems. It is intended to have atmospheric pressure, water temperature, water level, and heating system which are all supervised by a central station. During the offseason in the winter, what is the most frequent that these components must be inspected?
Solution | Posted 08/24/2020
c. Quarterly. Water Temperature (NFPA 25-2017 Section 22.214.171.124), Heating System (126.96.36.199), Water Level (9.2.1) and Temperature Alarm (188.8.131.52) all require no more frequent than quarterly inspections for the tank described.
Subscribe and learn something new each day:
Thank You to Our Top
February '21 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.