A building addition is to connect two existing buildings of different construction types. Which of the following construction type arrangements is always permissible?
a. Provide the least fire-resistive construction type of the connected portions with no fire barrier separation
b. Provide 1-hour vertically aligned fire wall is installed between them to create separate buildings
c. Provide any construction type for the connection portion with 2-hour fire barrier between buildings
d. none of the above
Solution | Posted 07/22/20
a. Least fire-resistive construction type of the connected portions, as described and permitted by NFPA 101-2018 Section 184.108.40.206.
To create separate buildings, a 2-hour vertically aligned fire barrier is required at a minimum, and use of any construction type is not always acceptable depending upon the size of the building, height, sprinkler protection, and other elements.
Subscribe and learn something new each day:
Thank You to Our Top
July 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.