At what frequency shall a preaction sprinkler system valve be trip tested with the control valve fully open?
b. every 3 years
c. every 5 years
d. every 10 years
Solution | Posted 07/20/20
b. Preaction sprinkler system valves must be trip tested with the control valve fully open every three years, per NFPA 25-2017 Section 126.96.36.199.2.
Subscribe and learn something new each day:
Thank You to Our Top
July 2020 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussions are open-ended fire protection, fire alarm, and life safety questions submitted anonymously for the benefit of sharing expertise and learning from other perspectives. Anyone can submit a question here:
2020 PE Prep Guide
PE Prep Series
2020 PE Prep Series
(Click to enlarge)
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.