Working on a list of areas that should have or require drain connections for coordination with plumbing. Here's what I have:
(1) plumbing standpipe to accept main drain, where the main drain can't be routed to the outside,
(2) floor drains in riser room as good practice; required if there's a pump or RPZ-type backflow,
(3) plumbing standpipe to serve drainage from fire standpipes, where they can't be drained to the outside, and
(4) standpipe or floor drain for remote inspector's tests & drains, where they can't be drained to the outside.
What am I missing?
Posted anonymously by a member for discussion. Discuss this | Subscribe
Subscribe and learn something new each day:
Thank You to Our Top May 2019 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
2019 PE Prep Guide
PE Prep Series
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.