A new Type II (000) construction facility without exposure protection is being designed to be built on an industrial campus. If Class II liquids are planned to be handled and dispensed regularly within the facility, what minimum distance from an adjacent, build-able property must the building allow?
a. 5 feet
b. 10 feet
c. 25 feet
d. 50 feet
Solution | Posted 06/13/19
Where an industrial application involves some uncertainty and deviation from standard practice and prescriptive code, but is without large uncertainties or extremely challenging applications, which of the following risk assessment approaches would be most appropriate?
a. Layer of protection analysis (FPS-LOPA)
b. Prescriptive standard application
c. Quantitative Risk Assessment (QRA)
d. Human reliability analysis (HRA)
Solution | Posted 10/04/18
A starch processing facility handles and processes starch dust. The plant's process has equipment which, under mechanical failure, could produce combustible dust in some areas of the facility. What type of truck would be permitted in these areas of the facility?
a. Electrical Type EE
b. Electrical Type ES
c. Diesel Type DY
d. Gasoline Type GS
Solution | Posted 10/03/18
For a performance-based design, a fire protection consultant makes an assumption that the production rate of carbon monoxide for a modeled fire package is equal to the highest production rate of each of the component fuels. This assumption would be considered:
a. explicit safety factor
b. implied safety factor
c. total safety factor
d. no safety factor
Solution | Posted 09/27/18
A new-construction church is to contain a main sanctuary and stage, complete commercial kitchen with lounge seating area, and a connected enclosed parking garage. What is the most hazardous occupancy for this facility?
a. Light Hazard
b. Ordinary Hazard Group 1
c. Ordinary Hazard Group 2
d. Extra Hazard Group 1
Solution | Posted 07/31/18
What is the minimum flammable & combustible liquid standard recommended spacing between an outdoor 120-foot diameter floating roof liquid storage tank of 7,000 barrels and a 100-foot diameter refrigerated dome roof storage tank?
a. 100 feet
b. 180 feet
c. 200 feet
d. 240 feet
Solution | Posted 07/25/18
Subscribe and learn something new each day:
Thank You to Our Top May 2019 Contributors!
Sprinkler Designer or Engineer?
Get all of our tools, including the Sprinkler Database, Friction Loss Calculator, Fire Pump Analyzer and more:
Daily discussion questions are open-ended questions posed by members for the benefit of sharing expertise and learning from other perspectives. Join as a member here.
2019 PE Prep Guide
PE Prep Series
Visit July-October for daily Fire Protection PE Exam sample questions.
Solutions are posted the day after posting.
Comment with your solutions, questions or clarifications.
Please note that questions posted are unofficial and in accordance with NCEES rules are intended to be similar to actual exam questions, not actual exam questions themselves.